- Variable speed
- Low power consumption
- Saves on OPEX
It is proposed for BTS sites where the acceptable inside temperature is 50 Deg C. The Design is suitable for various combinations of equipment’s within a shelter.
The Ventilation system will have main components Fan Out unit , Filter Unit and Controller unit. Filter unit to be placed on lower level w. r. t. floor preferably at door. Fan outlet unit should be placed on height closer to roof of shelter on diagonally opposite wall. Ensure that the Fan Unit is installed as possible near to BTS so as hot air gets directly escaped to atmosphere. Micro-controller with in-built intelligent logic is able to ON/OFF and control the speed of fan and ON/OFF upto 2 air-conditioners based on the Ambient and Shelter Temperature thereby air-conditioner run hours is reduced and bringing energy savings.
Cabinet DC Active micro cooling
To suit & satisfy the need of today’s telecom site energy conservation by converting Indoor site to Outdoor site without compromising the equipment functionality.
The DC Standard air-conditioner provides a suitable conditioning for equipment in cabinet or shelter maintaining a good temperature for operating.
GP outdoor battery cabinets are IP55 outdoor enclosures designed to work for telecom environmental conditions. The cabinets offer compatibility to diverse battery capacities and technologies. Their double skin and 4-point lock mechanism ensures complete protection of installed equipment. Advanced thermal cooling feature enables remarkable savings both in capital and operational expenditures.